This week- doing what we can to have you sorted for christmas
More on the analyser
are reading 7PPM and we are happy as long as it is below 500PPM so this is a good result. The ratio measures the difference between the CO2 and the PPM and as long as the reading is below 0.004 the boiler is still safe to be using, and as you can see from the picture the ratio is 0.0001 so this is the best result we can ask for.
In picture 2 we can see the Net efficiency (EFFN) and the Gross efficiency (EFFG). Looking at the Gross efficiency we would expect a new oil boiler to be running at this level, so all in all after a good clean this boiler was running as good as new!
Continuation of the bathroom
As you can see the bathroom is coming along nicely, however due to an unrelated injury it was unable to be completed this week. The shower tray is now bedded and the tiling is done, you can even see our apprentice building upon her tiling skills! All tiles were chosen by the customer and we have worked closely with him to design the bathroom just as he likes it!
Fitting gas bottles with a 4 Bottle Regulator Valve
Finally - our chimney
Keeping up to date with all the latest from Eco Dragon
We love pictures! By taking pictures regularly of work we are carrying out, we can be sure that you are seeing the best of what Eco Dragon has to offer. Remember, if you want to see the most recent pictures of our work then head on over to our Facebook page or check out our Facebook and Instagram feed on our home page!
Eco Dragon South West Ltd are proud sponsors of Hiryu Budou-Jyo (Flying Dragon Martial Arts Club)
Our plumbers, Heating Engineers and Construction Workers are based in St Austell and cover most of Cornwall!